Energy-absorbing chambers DN 625
Utility wastewater and stormwater energy-absorbing chamber
Outlet: DN/OD 160, 200 mm; Inlet: DN/OD 50-160 mm
Energy-absorbing chambers DN 625 for utility wastewater and stormwater systems. Made from polyethylene (PE) material with D400 class self leveling or stationary type cover.
- Inlet DN/OD 50 .. 160 [mm]
- Outlet DN/OD 160 .. 200 [mm]
- Cover: D400 class (40t), RAL GZ-692
No stagnant water in the chamber
Resistant to aggressive environment, no corrosion
Long service life (>50 years)
Flexibile for movements in soil (no cracking of the manhole)
Water-tightness > 0.5 bar, watertight materials
The diameter of access hole allows convenient and quick maintenance of sewerage networks
Intended for utility sewerage and rainwater pressure systems:
- SDR17, PE80 class EN 12201-2+A1 pipes with nominal pressure class PN8 [bar];
- SDR17, PE100 class EN 12201-2+A1 pipes with nominal pressure class PN10 [bar];
- SDR17, PE100-RC class EN 12201-2+A1, PAS 1075 pipe types- 1, 2, 3 with nominal pressure class PN10 bar.
Chamber installation according to: EN 1610, CEN/TR 1046
Construction work related to chamber cover and upper part of chamber shall be performed in accordance with road or territory manager’s issued technical regulations and sewer system operator (water management service provider’s) requirements.
- OUT 0° DN 160 - IN R/L° DN 50, 63, 75, 90, 110
- OUT 0° DN 200 - IN R/L° DN 125, 140, 160
Note: On demand it is possible to manufacture inlet “IN(R/L)°” with flange connection
Minimum instalation depth: 1.0 [m]
Maximum installation depth is up to 5.0 [m], if the ground water level is 2.0 [m] from the surface. If the ground water level is 0.0 [m] from the surface, the maximum installation depth is 4.0 [m], according to the requirements of EN 13598-2 standard.
Stationary type cast iron frame and cover, DN 600/746 [mm], installation class D400 (40t) corresponds to the requirements of EN 124-2 and RAL GZ-692 standard
Self-leveling type cast iron frame and cover, DN 700 [mm], installation class D400 (40t) corresponds to the requirements of EN 124-2 and RAL GZ-692 standard
Cast iron shell ring adapter corresponds to the requirements of EN 124-2 standard
Reinforced concrete height adjustmet ring, DN 665/1000 [mm], corresponds to the requirements of EN 206, EN 1917 and EN 1917/AC standard
Reinforced concrete support ring, DN 665/1060 [mm], corresponds to the requirements of EN 206, EN 1917 and EN 1917/AC standard
Chamber shaft and base:
Polyethylene (PE) chamber shaft, DN 625, h=400/600/900 [mm], corresponds to the requirements of EN 14802
Polyethylene (PE) chamber base, DN 625, h=900 [mm], corresponds to the requirements of EN 13598-2, EN 476
To ensure the water-tightness of the chamber, the connecting elements are connected with rubber sealing rings DN 625 [mm] corresponding to the requirements of EN 681-1 and EN 1277 standards. The chamber must ensure the maximum pressure of 0.5 [bar].
According to the requirements of EN 681-1 and EN 1277 standards, rubber sealing rings of chambers have to ensure water-tightness of connections at water pressure of 0.5 [bar].
|Self-leveling round cast iron frame and cover with ventilation openings DN 700 mm||on request|
|Stationary type round cast iron frame and cover with ventilation openings DN 600/746 mm||on request|
|Odour filter selection|
|Sewer air odour filter||820230000000000000|
|Shell ring adapter|
|Cast iron shell ring adapter for self-leveling cover||820215601ST7300038|
|Reinforced conrete support ring, DN 665/1060 mm, h=160 mm||821072666850000000|
|Reinforced conrete height adjustment ring, DN 665/1000 mm, h=60 mm||821073T09840000000|
|Polyethylene (PE) ring type shaft, h=400 mm||815024625390000134|
|Polyethylene (PE) ring type shaft, h=600 mm||on request|
|Polyethylene (PE) ring type shaft, h=900 mm||815024625450000134|
|Sealing ring, DN 625 mm||815026625000000000|
|Chamber base selection|
|PE Spherical energy-absorbing chamber base DN 625 mm||815054625450000134|
Product pictures are provided for informative purposes only.
Proportions and colours of the original production may differ from the pictures.